user, February 2, 2023
How to Calculate Weather-Normalized Energy Consumption
If you are an asset manager with properties in regions with different weather conditions or If you are a company with branches distributed over the whole country or different continents, such as hotel, gas station, and supermarket chains; You may need to review the energy consumption of your properties and have a reliable and fair metric to compare your branches to establish energy efficiency strategies and avoid revenue losses in your business.
In this blog post, we explain to you how we calculate this normalization via a standard method. This method will be also useful for managers who handle one commercial building and want to normalize their consumption over various seasons (Especially hotel managers).
Heating and Cooling Degree Days (HDD and CDD) is a unit of measurement that has been adopted by ASHRAE organization as the industry standard for weather models. HDD and CDD indicate how hot or cold is outside for a given day and for how long it was at that temperature. This can be more helpful than knowing the temperature alone for estimating how much energy you used on heating and air conditioning. National Grid notes that studying degree-day patterns can help energy managers to evaluate the oscillating trends in energy bills.
In order to calculate the HDD and CDD, you need to define your base temperature (the temperature at which your building needs no heating and cooling). For example 20 degrees in a city like Lisbon is the base temperature for most of the buildings (but it varies building by building related to natural sun lights and ventilation, age and construction material of the building). Then obtain the average outdoor temperature for a day (which is available online). If the average outdoor temperature is exactly equal to the base temperature (20 degrees), the HDD and CDD are zero. If it is above the base temperature, subtract it from the base temperature to find the CDD and If it is below the base temperature, subtract it from the base temperature to find the HDD. For example, if the high temperature of a day in Lisbon is 28 degrees and low temperature is 18 degrees, the average temperature is 23 degrees. Subtracting 23 from 20 equals 3, which indicates that there were 3 CDD for this day.
To normalize the electricity consumption of buildings base on HDD and CDD, the following steps should be taken: